>> 16 channels analog signal acquisition, isolated converter RS-485/232 output
>> 24-bit AD converter, accuracy>0.05%
>> 4-20mA/0-20mA current signal or 0-5V/0-10V voltage signal input
>> RS-485/232 interface can be programmed calibration module accuracy
>> Signal input / output:3000VDC isolation
>> Wide supply range: 8 ~ 32VDC
>> High reliability, easy programming, easy to apply
>> Standard DIN35 rail mounting
>> User-programmable settings module address, baud rate, etc.
>> Support the Modbus RTU protocol
>> AD conversion rate can be programmed
>> signal measurement, monitoring and control
>> RS-485 remote I / O, data acquisition
>> application of intelligent building control, security engineering
>> industrial automation control system, the RS-232/485 bus
>> Industrial signal isolation and long-term transmission
>> equipment operation and monitoring
>> measurement of sensor signals
>> the industrial data acquisition and recording
>> medical, industrial and product development
WJ29 - U(A)□ - □
Input voltage or current signal Communication Interface
U1: 0-5V A1: 0-1mA 485: RS-485 output interface
U2: 0-10V A2: 0-10mA 232: RS-232 output interface
U3: 0-75mV A3: 0-20mA
U4: 0-2.5V A4: 4-20mA
U5: 0-±5V A5: 0-±1mA
U6: 0-±10V A6: 0-±10mA
U7: 0-±100mV A7: 0-±20mA
U8: user-defined A8: user-defined
Part No.:WJ29-A4-485 (means 16 channels 4-20mA input,ouput is RS485 interface)
Part No.:WJ29-U1-232 (means 16 channels 0-5V input,output is RS232 interface)
Part No.:WJ29-U2-485 (means 16 channels 0-10V input,output is RS485 interface)
Part No.:WJ29-U8-485(U8:0-12V) (means 16 channels 0-12V input,output is RS485 interface)
How to set Modbus RTU communication protocol:
Module default protocol is character communications protocol. If you need to set the module to Modbus RTU protocol, please follow these settings:
1. Put INIT switch to INIT position.
2. Connect the power cord and the communication interface cable.
3. Turn on the power, the module enters the default state automatically, address 00, baud rate 9600.
4. Wait 5s, module is initialization.
5. Send the command $00P1(cr), check the response, if is !00 (cr), set successfully.
6. Turn off the power, INIT switch to the NORMAL position.
7. The module has been set to the Modbus RTU protocol mode successfully.
AD conversion rate: 80 SPS (factory
default, the user can send commands to modify the conversion rate)
You can set the AD conversion
rate 2.5 SPS, 5 SPS, 10 SPS, 20 SPS, 40 SPS, 80 SPS, 160 SPS, 320 SPS, 500 SPS,
1000 SPS command. (Channel conversion rate = AD conversion rate / Open numbers
NOTE: after Modify the conversion rate,
need re-calibration module, otherwise the measurement data will be biased. You
can also specify the conversion rate when ordering, we press the conversion
rate you require recalibration in the factory.
Note:when you order ,please choose your input and output or note your Part No..
Download Datasheet : WJ29 series 16 Channels AD Converters.pdf